Chula Vista Medical Center (Hospital)
Total Annual Savings:
Capital Upgrade - HVAC and Controls System Replacement
HVAC equipment and controls at Birch Patrick Convalescent Center are in very bad condition and should be replaced. The air handlers do not have control valves and water flow is set using a manual valve. This building was designed as a variable air volume (VAV)/reheat building with controls, but was actually built as a constant volume/reheat building with local pneumatic zone control. Consider this building for complete HVAC system replacement.
See above Description.